Section 7 1 G. Cleanouts
SECTION 7 SANITARY SEWER GRAVITY COLLECTION SYSTEM
Commercially manufactured wye branches and fittings shall be used to connect to the sewer main. Cleanouts on house laterals shall be located in the right-of-way as close as possible to the property being serviced. A City approved box and cover, according to City Standard Details, shall be used over the cleanout. The top of the cleanouts shall be a maximum of 6 inches below finish grade and have a threaded brass plug with a protruding integrally cast square nut. Plugs with recessed holes for tool grips shall not be used.